Type: Posts; User: Sierrasparky
How can you hog that much out of a deck plank and still have integrity?
You cannot strip the sheathing of NM type wire and install in a conduit. It's not rated for such.
If the conduit is a sleeve you just leave on the sheath.
If I may ask , What is the reason for the question?
Of course it did not have good connection. These guys always have the answer you cannot cross examine unless you were present.
Ethical test, Really!
That's an abuse of a test and requirement. The EE that draw the plans I see have no ethics.
It must go like this:
What do you do when you "have" to draw something...
Yea, That is the problem. He is Educated and a professor and does not know what he is talking about. He commands authority be cause he has certain degrees and background. Nobody would be willing to...
Here is that uninformed and ignorant investigators email:
who says Most are self grounding. I have to be very specific when purchasing receptacles that are self grounding.
On a second look at that picture-
Does that AC cable look like from the 2000's.
Those conductors look like they are TW?
Another false and misleading investigation.
No ground- what malarkey , its AC cable and approved for ground.
Who knows if those outlets were self grounding. Who knows if the receptacle made...
How does that exception work in the 2014. I see that is all about service wires and not disconnects?
So basically a can of worms.
Is there a situation where you have no choice but to wire IS?
In a Sewage lift station Class 1 Division 1 Group D ,is it assumed that the Float switches in the tank are to be intrinsic?
EMT for single family dwelling too?
Cheap LED's ?
Never completely trust those things. You'll get bit.
Not seeing the show, I would assume that price was for rough in only as they probably already budgeted to install new fixtures and such. No new panel, striped to the studs. That is a one day deal on...
no way to escape AFCI other than your PDU suggestion.
Don't see the big deal with new circuit and AFCI.
You can use a AFCI outlet off a panel that does not accept a AFCI breaker and then run the...
here in CA it's been required. We have code section and I believe it is in the 2011 NEC
GFCI protection. Outlets supplying pool pump motors connected to single-phase, 120 volts...
I am amazed as to how many people think that as long as they send out a 1099 that it makes it legit.
I guarantee that every state has guide lines mirroring the IRS for who can be an independent...
You don't think that signing a statement that the employee was paid under the table no taxes and no workers comp paid is no big deal?
We'll that is an Automatic suspension of ones license in this...
I remember seeing that stuff at a trade show. They called it Smart glass.
The display showed the privacy glass but I remember something about solar heat gain.
I forgot to ask...
If there was workers comp there would be records of hours worked!:ohmy:
Does this Guy really want to go in front of the board and state that he worked as a 1099 independent contractor...
usually for Privacy