I have always used 1.5 KVA / ton as a rough guestimate for a typical small unit.
I think I like suemarkp's formula better (if you happen to know the EER).
Add electric heat, humidification, or energy recovery and the KVA skyrockets. As others have said, using a guestimate can lead to trouble, so use with caution.
Naw i wanted to know the rough estimate. I was guessing about 6-8 KVA for a 5 ton.
The reason for this was, i have recieved load sheets from electricians who have stated that the 5 Ton ac consumes 9.9 KVA x 3 = a ridiculous 29 KVA.
I have recieved a load sheet yesterday stating that a 5 Ton AC was 9.0 kVA x 2 = 18 kVA
So when i replied back and told the guy he is " double stating " his AC loads, i wanted to make sure what i was saying was right.
It makes a huge difference considering he was alloting eight 5 ton AC's 18 kVA each. That is about 45 kVA extra just on AC's
I know about the SEER ratings and stuff but i just wanted to make sure that
1 Ton is about 1.5 KVA and not something like 4 kVA
Thanks for the responses.
Those ratings wouldn't be unusual for a unit with electric heat, a humidifier, or a energy recycler.
Check out this website:
It looks like 1 ton is approx. equal to 3.5kW
1 ton = 12,000 BTU/hr
12,000 BTU/hr = 3.514kW
Therefore 1 ton = 3.514kW
and 5 tons = 17.57kW
Again, this doesn't work for calculating power use of an air conditioner. See post #9. An air conditioner or heat pump may seem like a perpetual motion machine, but they are not converting energy, they move it.
What I think that website is trying to say is if you have electrical equipment which uses 10KW of power, you're going to need 2.8 tons of cooling to remove that heat.
Also, the EER rating simply refers to how much it will cost to operate the unit when it is running, and varies with every model or manufacturer. The size (tons) of the system is the determining factor on how well the A/C will cool your room.
The Energy Efficiency Ratio (EER for air conditioners, SEER for central air conditioning systems)tells the user how much energy is consumed compared to the heat energy removed from the space. See the formula.
BTU heat removed from a spaceEER= --------------------------------Watts input to the equipmentBack to the OP, he wants to know the correct power needs for a 5 ton A/C unit. IMO, 18kW is correct for a 5 ton ACU.
Rules of thumbs are based on experiences; say 2kVA per ton (10kVA on your case) can accommodate your 5 tons ACU if this 5-ton size is a design bigger than the actual cooling requirement of the installation. The temp settings will correct the cycle time of the refrigerant pump and the cooling mode selector will be selectable to a lower refrigeration pump/condenser fan speed; all leading to a smaller demand factor.
Hope this clears all doubts.
I still say put the calculators down and plug in one horsepower per ton and you're going to be damn close. If you need more accurate than that, get cut sheets or look at the dataplate.
For some datapoints:
From page 3 for a 14 SEER Goodman air conditioner - a 5 ton unit draws 26.4 amps for the compressor and 1.6A for the fan. So the VA for this unit at 240V is 6720.
From page 5 for a 12 SEER Bryant heat pump - a 5 ton unit draws 27.6 amps for the compressor and 1.4A for the fan. So the VA for this unit at 240V is 6960.
This is nowhere near 18 KW but real close to the 1 HP per ton which MD uses.
Should have divided the thermal calc results by coefficient of performance.
18 kW / 3.43 = 5.248 kW (electrical). Very close to A/C unit power consumption rates.
I just don't feel comfy with rules of thumbs.