my question is about sizing conductors for a 1600 amp single phase service.
would 4 - # 500 MCM copper THWN-2 RATED FOR 90 C per phase be adequate
the run is less than 6 feet from ct cabinet to service disconnect
the allowable ampacities chart says 500 mMCM is good for 430 amps x 4 = 1720
Thanks for any comments