The GEC is connected in the enclosure where the grounded and grounding conductors are connected to each other. The grounding and grounded conductors, in the case of a transformer, can be connected to each other at either the transformer or the OCPD, but not both. No mater where the GEC is connected, a bonding jumper will be required between the transformer and the OCPD.
Originally Posted by erickench
"It is the first responsibility of every citizen to question authority." B Franklin