Hi everyone, hope everybody had a great memorial day.
I am working on designing a commercial project and just got two rejections from the city.
#1 - Says I need GFCI protection for the drinking fountain.
#2 - Says I need GFCI protection for the refrigerator (which is in break room)
#1 - I know in the 2008 NEC section 422.52 was added, requiring drinking fountains to be GFCI protected, however, does anyone know if the manufacturers are making the fountains with protection built in?
#2 - He cites 210.8(B)(5) for this one, which is under sinks. The refrigerator is within 6 ft of a sink, however isn't it true the refrigerator receptacle does not have to be protected?