Deja Vu, Roger and I had this conversation last night. No I do not agree. Reason being if you are on gen. power the gen. could care less about the utility neutral. The return current wants to go back to the source,being the gen. The simple way to look at the whole system in a non separately derived system is to pretend every thing past the main service disconnect is a sub panel. the gen is a sub, the transfer switch is a sub. The same rules apply that the neutral and EGC are only bonded in the first disconnecting means. After that every thing is separated to prevent unwanted currant on metal parts.
Originally Posted by kohler_guy
Organized people are people that are just too lazy to look for their stuff