just apply 230.28 to 230.43 and you will have the only available requirement in the NEC, but almost all utility's will have a standard that will apply if you want them to hook up the electric.
Originally Posted by inspector 102
Also remember 230.28 only applys if the service riser mast supports the service drop conductors, if the drop is attached to the side of the house then only 230.43 applys, and of course the utility standard.
Last edited by hurk27; 08-20-10 at 10:14 PM.
Wayne A. From: N.W.Indiana
Be Fair, Be Safe
Just don't be fairly safe