What's the consensus. If ungrounded conductors are increased in size due to voltage drop concerns, is the neutral or grounded conductor also increased?
I know the equipment ground must be upsized per NEC 250.122(B). I'm thinking the answer is yeas based on 240.23. Although the term "shall be permitted" rather than must be, or is required has got me thinking.
Thoughts and input are greatly appreciated.