How many here are still running indoor NM cable in a Carflex or sealtite sleeve to a piece of outdoor equipment? I have been doing it for years and never had an issue with it until now. Seems as though now we have to either transition to THHN or UF type cable for this application. Inspector is considering it a damp location and will not allow indoor NM to be used. Have I been violating the code all along, or has it just not been enforced. Thanks.