Have a row of Electrical disconnect's ( 7 - 30 amp 480V ) that feed various immersion heaters in process tanks in a Anodize room . Management seems to think that material on carts can be pushed up to the disconnect's as long as carts have wheels and can be pushed out of the way . I say OHSA can write us up for this for not maintaining the proper clearance . We are into lean and Kaizen and reducing the " FOOT PRINT " . This is starting to become a regular issue . Would like to get some opinions on this .... PS. Would also like to say thanks for the help every one gives on questions , I do appreciate it .