Did we ever hear what size wire the plans call for? Most jobs I've bid tell you the wire size somewhere.
Lou (wannabe economist)
If you relentlessly pursue perfection, you will eventually catch excellence.
I was just awarded a job. The plans may be complete next week.
i haven't drawn them yet.
it was my shortfall, i didn't realize the repeaters would pull that much.
i was figuring a nominal 180 watts per device, a quad would give 360 watts, or three amps.
i am now the proud owner of six rolls of #6 simpull, and three rolls of #8 green simpull.
$2,200 or so.
next time, i'll clarify something like that.... 'eh, it's only THREE OUTLETS, not even something to consider.... ;-)
~New signature under construction.~
~~~~Please excuse the mess.~~~~
If this is a 60 amp circuit using 6 AWG conductors - the equipment grounding conductor can be 10 AWG.
Just doesn't quite sound right does it? But that is what code says.
A code compliant way to use the 10 AWG EGC is to run a feeder to near the outlet with 10AWG EGC. Then run shorter 20 amp branch circuit to the outlet with smaller conductors.
Last edited by kwired; 05-30-12 at 10:28 PM.