Heres a pic that might help.
Your equipment grounding conductor accompanying your 480 v supply is the grounding means on the primary side.
Most often here, E/Cs bond their grounded conductor at the transformer and install a grounding electrode to that point (upper diagram). 250.30(A)(7) will prescribe your electrodes, but building steel is a common one.
At my age, I'm accustomed to restaurants asking me to pay in advance, but now my bank has started sending me their calendar one month at at time.