That's the point I was trying to make.
Originally Posted by chris kennedy
To be rational, stickers are placed on the face plate, in spite of what the NEC says.
To be punctilious, either the stickers would be on the back of the receptacle, or there would be gnat sized writing on the front, like the people at the circus do when they write your name on a grain of rice.
Cheers and Stay Safe,
Marky the Sparky
OSHA 1910.304(g)(2)(iv) "One phase conductor of a multiphase system where one phase is grounded shall be grounded"