Originally Posted by chris kennedy
The two disconnects are located back to back and connected to a gutter with main wires from meter.
Originally Posted by hurk27
no, I didn't get the inspector blessing, the main disconnect for the new meter needs to be outside next to the new meter, what inspector recommended was to leave the CT meter and riser as the way it is and add the new meter with his own over head riser and a main disconnect next to the existing CT meter. Thank you
What is reasoning for separate meter? If to supply a separate occupancy and if disconnecting means are not required to be grouped together it may be ok, really need to more before I can make that call. If disconnects are required to be grouped together then inspector is creating violations before you even get started by wanting one disconnect in this location and other(s) at existing location.
Originally Posted by O'donisR
Tags for this Thread