Looked at a service the other day, the meter was located after the service disconnect. The grounded conductor was never bonded to the service disconnect enclosure, it was passed through into the meter enclosure where it was bonded to the meter enclosure and a #8 bonding jumper was brought back to the service disconnect for bonding. I'm ordering a ground lug kit for the disconnect, however how do I handle the meter enclosure? I don't know if there is a way to separate the equipment grounds and neutrals at the meter enclosure. PVC was used between meter and service enclosures.