Originally Posted by iwire
It's the same here, we can't work on elevators.
If I were to run 208V 3 phase to a disconnect then I would label the disconnect with the voltage provided and that's it for me. I run whatever is shown on a drawing or provided on the work order.
I think that if an elevator company had the electrician doing more than that it would be wrong.
All things are subject to interpretation, whichever interpretation prevails at a given time is a function of power and not truth...Nietzsche,,, Ain't it the truth.... Growler