Notice that 240.21(C) does not give blanket permission to not protecting the secondary in a two-wire to two-wire transformer connection. The transformer ratio must be taken into account.
As far secondary grounding, if your choose not to ground the secondary 250.21(B) would come into play.
I think an argument can be made that 240.20(B)(1) would require you to use the mid-point as a ground, however, I have seen it ignored and a two-wire secondary only being used.
At my age, I'm accustomed to restaurants asking me to pay in advance, but now my bank has started sending me their calendar one month at at time.