1. Member
Join Date
Feb 2017
Location
Maine
Posts
75

## AC PV wire

Could we use PV wire in ac solaredge output?

2. Senior Member
Join Date
May 2011
Posts
4,192
I suppose you could. I'm not sure what the point would be.

You would have to run the conductors together in a raceway and account for the non-standard diameter if calculating conduit fill.

3. Member
Join Date
Feb 2017
Location
Maine
Posts
75

## AC 6awg cable tray

Originally Posted by jaggedben
I suppose you could. I'm not sure what the point would be.

You would have to run the conductors together in a raceway and account for the non-standard diameter if calculating conduit fill.
Really the issue is 1/0 size in cable tray minimum, NEC allow you PV wire in cable tray less than 1/0. But I am not sure if inverters output are included

4. Senior Member
Join Date
May 2011
Posts
4,192
Originally Posted by jjavier
Really the issue is 1/0 size in cable tray minimum, NEC allow you PV wire in cable tray less than 1/0. But I am not sure if inverters output are included
They are not. That section specifically refers to pv source or output circuit and an inverter output circuit is not one of those.

5. Member
Join Date
Feb 2017
Location
Maine
Posts
75
Originally Posted by jaggedben
They are not. That section specifically refers to pv source or output circuit and an inverter output circuit is not one of those.
ok thanks

6. Senior Member
Join Date
May 2013
Location
Massachusetts
Posts
2,312
Originally Posted by jjavier
Really the issue is 1/0 size in cable tray minimum, NEC allow you PV wire in cable tray less than 1/0. But I am not sure if inverters output are included
You can use multiconductor type TC cable for this application, if you do desire to use a cable tray. And not have to use 1/0 and larger.

I don't understand why there needs to be an exclusion of AC, when using PV wire of all sizes in a cable tray. Or why we have the 1/0 and larger rule in the first place. As in, what physical hazard happens because of it?

7. Member
Join Date
Feb 2017
Location
Maine
Posts
75

## Tc cable

Originally Posted by Carultch
You can use multiconductor type TC cable for this application, if you do desire to use a cable tray. And not have to use 1/0 and larger.

I don't understand why there needs to be an exclusion of AC, when using PV wire of all sizes in a cable tray. Or why we have the 1/0 and larger rule in the first place. As in, what physical hazard happens because of it?
That is the issue.

We have to use 6AWG copper in solaredge ac, and on the roof, it´s very hard to comply with the amps (50.1Amps in 6awg).

The roof will have restricted access. Can we use cable tray (TC )(5 conductors) on the solar roof? Must be covered if it is UV resistant?

8. Senior Member
Join Date
May 2013
Location
Massachusetts
Posts
2,312
Originally Posted by jjavier
That is the issue.

We have to use 6AWG copper in solaredge ac, and on the roof, it´s very hard to comply with the amps (50.1Amps in 6awg).

The roof will have restricted access. Can we use cable tray (TC )(5 conductors) on the solar roof? Must be covered if it is UV resistant?
FYI, the neutral doesn't count as a CCC in this application. With a typical temperature derate from 75A at 90C, 3.5" above the roof, the #6 Cu should have enough ampacity if you have a dedicated conduit for each inverter.

In any case, the UV resistance and the restricted access, should be enough not to need a cable tray cover.

#### Posting Permissions

• You may not post new threads
• You may not post replies
• You may not post attachments
• You may not edit your posts
•