1. Senior Member
Join Date
Oct 2009
Location
Austin, TX, USA
Posts
9,421
Originally Posted by infinity
I would guess that the answer undefined wasn't on the test so you would need to look for the theoretical answer which should be 0 since it says that it's ungrounded.
That's not the theoretical answer. 0V says that they are at the same potential, i.e., the conductor on which you are measuring the voltage to ground is grounded.

2. Question 3, this may help
pg 4, fig 6-6
http://static.schneider-electric.us/...tion6_0307.pdf

3. Originally Posted by ggunn
That's not the theoretical answer. 0V says that they are at the same potential, i.e., the conductor on which you are measuring the voltage to ground is grounded.
So if I take my Wiggy and go from any phase to ground it will read what? In my mind the author of the question was thinking ungrounded = 0 volt to ground from the B phase. If we knew the answer choices that would clear it up.

4. Originally Posted by infinity
So if I take my Wiggy and go from any phase to ground it will read what?
Very likely a different reading then if you had a high impedance meter.

5. Moderator
Join Date
Dec 2012
Location
Placerville, CA, USA
Posts
19,233
Normal stray capacitance will cause the ungrounded three phase to float very close to ground.
For an ungrounded 240V delta, A, B, and C will be about 139V to ground on a high impedance meter.

Sent from my XT1585 using Tapatalk

6. Originally Posted by GoldDigger
Normal stray capacitance will cause the ungrounded three phase to float very close to ground.
For an ungrounded 240V delta, A, B, and C will be about 139V to ground on a high impedance meter.

Sent from my XT1585 using Tapatalk

The link I posted gives a good explanation

7. Junior Member
Join Date
Jul 2017
Location
Glen Rock, Pa
Posts
10
Originally Posted by infinity
So if I take my Wiggy and go from any phase to ground it will read what? In my mind the author of the question was thinking ungrounded = 0 volt to ground from the B phase. If we knew the answer choices that would clear it up.
Cant recall exactly, but i do remember 0, 240 & 208 being choices. I went back and forth between 0 & 208, finally choosing 208 because there would have to be some kind of grounding system, whether it terminated in xo of that secondary, the primary, or ges to the service. At least that was my thinking, under the gun, at the time. Thanks for the great responses.

8. Junior Member
Join Date
Jul 2017
Location
Glen Rock, Pa
Posts
10
240/sqrt3=139.
cant recall if that was a choice.
thanks ingenieur!

9. Senior Member
Join Date
Feb 2004
Posts
643

conductor parallel . queston #4

Originally Posted by gunpowder
4. What's smallest size conductor allowed in parallel? I chose 1/0, but couldn't also be 6awg for gec?

Sent from my SAMSUNG-SM-G891A using Tapatalk
The smallest conductor allowed in parallel is 20 awg.

10. Originally Posted by domnic
The smallest conductor allowed in parallel is 20 awg.
Maybe some esoteric rule or exception says that, but most tests would want 1/0 per 310.10(H).

Posting Permissions

• You may not post new threads
• You may not post replies
• You may not post attachments
• You may not edit your posts
•