# Thread: Unit 10 Electrical exam Prep book 2014 cycle

1. Junior Member
Join Date
Sep 2017
Location
Meridian Idaho. United states
Posts
1

## Unit 10 Electrical exam Prep book 2014 cycle

I have a question about The last example on page 299 or 300 of the 2014 Electrical exam preparation guide book.

the question is: "What's the demand load for ten single-phase 12 KW 208V ranges on a three phase service."

In step one, determine the maximum number of ranges between any two phases: 4

How did they arrive at that?

2. Moderator
Join Date
Dec 2012
Location
Placerville, CA, USA
Posts
19,542
You have to assume that an attempt will be made to balance the load across all three phases.
Each unit will get 208V from two legs of a 208Y/120 service.
Equal distribution would be 3-1/3 ranges on each phase, so the closest we can get in real life will be four on one phase and three on each of the other two. The maximum number for any phase in the group will then be 4.
You could put all ten on one phase, ignoring balance but that is not the interpretation of maximum number that the code is looking for.

#### Posting Permissions

• You may not post new threads
• You may not post replies
• You may not post attachments
• You may not edit your posts
•