# Thread: Test question

1. Senior Member
Join Date
Mar 2007
Location
Raleigh, NC
Posts
136
Mentioned
0 Post(s)
Tagged
0 Thread(s)

## Test question

A combination load consisting of 15KVA of resistance heat and a motor rated 1.2KVA is served by a 240v branch circuit. What is the minimum required rating for this branch circuit?

I get 84 amps. Test booklet says the answer is 90. What say you guys?

2. Originally Posted by blueheels2
A combination load consisting of 15KVA of resistance heat and a motor rated 1.2KVA is served by a 240v branch circuit. What is the minimum required rating for this branch circuit?

I get 84 amps. Test booklet says the answer is 90. What say you guys?
You have to size it according to breaker sizes. Look at 240.6

3. Senior Member
Join Date
Mar 2007
Location
Raleigh, NC
Posts
136
Mentioned
0 Post(s)
Tagged
0 Thread(s)
Originally Posted by Little Bill
You have to size it according to breaker sizes. Look at 240.6

Thanks I was thinking it was asking for load to be considered when sizing the ocpd.

4. Originally Posted by blueheels2
I get 84 amps.
Perhaps I need more coffee this morning. But I don't see how you came up with 84.

Taking the motor at 125% of 1.2 KVA gives you 1.5 KVA. Add 15 KVA for the heaters and you are up to 16.5 KVA. If this is single phase, then 16.5 KVA / 240 V = 68.8 amps. If this is three phase, then divide again by 1.732 and you get 39.7 amps.

Please explain your math, while I go pour myself another cup of wake up juice.

5. Senior Member
Join Date
Mar 2007
Location
Raleigh, NC
Posts
136
Mentioned
0 Post(s)
Tagged
0 Thread(s)
15000 + 1200= 16,200 ÷ 240= 67.5 x 1.25 because it's a continuous load gives you 84.375A.

Edited to add you calculated the motor as continuous but the heaters are considered continuous as well based off of 424.4 (b) I think.

6. Senior Member
Join Date
Apr 2009
Location
Williamsburg, VA
Posts
6,042
Mentioned
0 Post(s)
Tagged
0 Thread(s)
Originally Posted by blueheels2
15000 + 1200= 16,200 ÷ 240= 67.5 x 1.25 because it's a continuous load gives you 84.375A.

Edited to add you calculated the motor as continuous but the heaters are considered continuous as well based off of 424.4 (b) I think.
Yes, fixed space heating is considered a continuous load. That said, there is no 85 amp breaker, so you must go to the next size up which is a 90 AMP.

That also said I do not see how you could put both of those loads on the same circuit, unless they were a package deal like an HVAC unit.

Edited to add... When posting test questions, it is incredibly important to post them completely as written... Not saying you didn't, just that even a missing, in the wrong place could change the answer

7. Senior Member
Join Date
Mar 2007
Location
Raleigh, NC
Posts
136
Mentioned
0 Post(s)
Tagged
0 Thread(s)
Originally Posted by JFletcher
Yes, fixed space heating is considered a continuous load. That said, there is no 85 amp breaker, so you must go to the next size up which is a 90 AMP.

That also said I do not see how you could put both of those loads on the same circuit, unless they were a package deal like an HVAC unit.
I would agree. This is just the questions you have to answer to get a license in NC.

#### Posting Permissions

• You may not post new threads
• You may not post replies
• You may not post attachments
• You may not edit your posts
•