# Thread: I need help with this HVAC label.......

1. Senior Member
Join Date
Apr 2016
Location
WA
Posts
306
Mentioned
0 Post(s)
Tagged

## I need help with this HVAC label.......

I can clearly see MOPD is 40A for this 460V 3 phase compressor.

Next I see Minimum Circuit Ampacity is 31.9A

Two or more people told me that this is the load. I disagree.

The load is Fan Motor FLA(1.0*2) + Compressor Motor RLA (7.3+10.3) =19.6A

Who is correct????

2. Member
Join Date
Oct 2013
Location
MD
Posts
84
Mentioned
0 Post(s)
Tagged
I would use MCA divided by 1.25 for load.

https://www.titus-hvac.com/softwares...ecalculate.pdf

3. Senior Member
Join Date
Oct 2015
Location
US
Posts
824
Mentioned
1 Post(s)
Tagged
The math is already factored in there use a 40a breaker or fuse with conductors suitable for 31.9 amps

Sent from my SM-G950U using Tapatalk

4. The MCA is the largest component (usually the compressor) *125% + the other loads. Curious as to why do you need to know the actual load?

5. Originally Posted by infinity
The MCA is the largest component (usually the compressor) *125% + the other loads. Curious as to why do you need to know the actual load?
How about for feeder and service calculations?

6. Originally Posted by kwired
How about for feeder and service calculations?
Could be that's why I asked.

7. Originally Posted by dionysius
I can clearly see MOPD is 40A for this 460V 3 phase compressor.

Next I see Minimum Circuit Ampacity is 31.9A

Two or more people told me that this is the load. I disagree.

The load is Fan Motor FLA(1.0*2) + Compressor Motor RLA (7.3+10.3) =19.6A

Who is correct????
19.6 is the maximum load it is rated for. Conditions of operation will determine actual load, but should not exceed that. Not sure just how they came up with MCA of 31.9, unless there is other load not on the nameplate for some reason. It is usually 125% of largest load plus all other loads. Even taking both compressor figures x 1.25 still doesn't get us all that close to 31.9.

8. kwired, I agree, that MCA is a puzzlement.

9. Senior Member
Join Date
Apr 2016
Location
WA
Posts
306
Mentioned
0 Post(s)
Tagged
Originally Posted by nickelec
The math is already factored in there use a 40a breaker or fuse with conductors suitable for 31.9 amps

Sent from my SM-G950U using Tapatalk
Elaborate on why you believe 31.9A is the running load. It cannot be that since it would heat up the wire.

10. Senior Member
Join Date
Jun 2003
Location
Hawthorne, New York NEC: 2014
Posts
4,229
Mentioned
1 Post(s)
Tagged
Running load is 19.6, the nameplate says wire it with conductors suitable for 31.9, not that the running load is 31.9, and use a maximum of a 40A breaker. So if you could find a 35A three pole you could use it.

Apparently they are designing for the max starting draw and voltage drop.

-Hal

#### Posting Permissions

• You may not post new threads
• You may not post replies
• You may not post attachments
• You may not edit your posts
•