Re: Hot Tub GFCI / Disconnect Location
If this is a single-family dwelling then a emergency disconnect is not required as per 680.41 This eliminates the 5' requirment.
Then all that is required is a service disconnect. And this only has to be within sight or be able to be locked in the off position. I think most disconnects have a place to put a lock on the cover door that would comply very nicely.
[ June 01, 2004, 12:51 AM: Message edited by: hurk27 ]
Wayne A. From: N.W.Indiana
Be Fair, Be Safe
Just don't be fairly safe