For an in-ground pool installation, with a 1.5 Hp(240v) pump hardwired to a 2-pole 20 amp breaker, the electrician installed a 120v GFI duplex convenience outlet adjacent to the pump. The outlet is not wired to it's own circuit breaker, but connected it across one leg of the motor circuit. IS THIS OUTLET WIRED PER ACCEPTABLE NEC PRACTICES? (all conductors to the motor look like they are #10. The motor is ~75 ft. from the breaker panel.)
Thankyou for consulting.