In CA: 1117.B.6 5.1 & 5.2 of the California Building Code.
Electrical switches: The center of the grip of the operating handle of controls or switches intended to be used by the occupant of the room or area to control lighting and receptacle outlets, appliances or cooling, heating and ventilating equipment, shall be 48 inches above the floor or working platform.
Electrical receptacle outlets: The center of electrical receptacle outlets on branch circuits of 30 amperes or less shall be installed not more than 48 inches nor less than 15 inches above the floor or working platform
I can build anything you want if you draw a picture of it on the back of a big enough check.
There's no substitute for hard work....but that doesn't mean I'm going to give up trying to find one.
IAEI / CEI / C10
Certified Electrical Inspector