406.8(A) and (B) 2008NEC
I don't recall anyone pointing this out, so I will.
In both damp and wet locations, all 15 and 20 amp, 125 and 250v non-locking receptacles will be required to be a listed weather-resistant type.
Combined with everyone's favorite 406.11 (Tamper-resistant receptacles in dwelling units), Dwellings are going to need tamper-resistant, weather-resistant receptacles outside.
Anyone even make these yet?
John from Baltimore
"One Day at a Time"
Responses based on the 2008 NEC
If you can stay calm, while all around you is chaos...then you probably haven't completely understood the seriousness of the situation