I intend on using a Three Phase Size 1 Full Voltage Non-Reversing Starter to power up a 120V Single Phase pump motor (1/3HP). I intend on using two of the poles on the Three Phase Breaker and two of the poles on the Contactor for the connection. I also intend on not using the CPT and hooking up the control wiring (120V) of the starter directly to the each phase leg. Will this cause any malfunctions in the operation of the Breaker and/or the Contactor? Does anyone know of any issues that may affect the proper operation of this setup?