Does the NEC address minimum coverage requirements for low voltage concrete-encased conduit? Table 300.5 seems to apply only to direct-buried conduits, and Figure 310.60 applies to medium voltage conductors. I have a 480V ductbank that was designed for 18" minimum coverage, but field conditions necessitate a shallower installation. I'm trying to determine if there are Code implications. . . .