I am running a 120v/20a circuit 500ft for a gate operator. Using copper and a 3.6volt loss in the Vd calculation I get a wire size of #1awg. The ground would calculate to the same using 250.122(B). Is this correct? It sure does not seem so!!
I am running a 120v/20a circuit 500ft for a gate operator. Using copper and a 3.6volt loss in the Vd calculation I get a wire size of #1awg. The ground would calculate to the same using 250.122(B). Is this correct? It sure does not seem so!!
The resistance of copper wire at 20 deg C is about 14% less than at 60 deg C. I assume in your application the conductors would be running closer to 20 than 60 deg C? If so, that would probably be enough to let you use #2s and still meet your spec. (but admittedly still a lot of copper to buy for a 20A circuit). I would expect a significant reduction in temperature rise from self heating with #2s vs. #12s for example, because of the roughly 1/10th power dissipation per foot (at a given current) and the larger surface area of the wires. That is, unless you're planning to run it with other circuits that significantly increase the temperature of the conductors.
At my age, I'm accustomed to restaurants asking me to pay in advance, but now my bank has started sending me their calendar one month at a time.
If the opener has a battery, the power merely recharges it, so you can practically ignore the voltage drop; maybe use #10.
Disclaimer: this opinion is only my own, so take it with the appropriate amount of wariness.
Master ElectricianCode references based on 2005 NECLarry B. Fine
Electrical Contractor
Richmond, VA
If you have 240V available, another alternative would be to run #10s and take about a 5% voltage drop to 228V. Then use a transformer with a 228V input tap and a 120V output:
https://www.galco.com/buy/Jefferson-...?scrollTo=docs
I just ran a 120V circuit out to a scoreboard 300 Ft. current drawn is 3.5 amps total. Using #10 I have a 1.85 voltage drop.
Works fine. You should be ok with #10 if amperage is low.
Bookmarks