Gotcha. Look to be sure they are TR receptacles.I just need some confirmation before I delve into a Kitchen where the customer wants to remove backsplash receptacles and install an angled plug strip that will not accept GFCI device.
I think I know that a 120v GFCI breaker will not correctly so I was thinking that a 240v GFCI should work, just needed to bounce it off others, I work alone so everyone here is it.
Gotcha. Look to be sure they are TR receptacles.
Customer has in possession the Task Lighting TR Series strips.FYI they do make GFCI TR plugmold strips. It is not angled though.