Thats how I read it i figured hood might be considered fixed in place appliance. If they had a 3rd 20amp circuit say for dining room could it go on that. IMO yesYou are correct.
No Other Outlets. The two or more small-appliance
branch circuits specified in 210.52(B)(1) shall have no other