Recently saw where a panel screw in front panel embedded itself into a cable causing an arc flash. Is there a minimum distance of cables from font of panel? I've been told there are both NEMA and NEC violations but can't find a specific standard. Panel was being reinstalled after an inspection. Thanks for any help.