Got a situation where will be moving a 120/240 residential panelbox. Would like to splice the #4 stranded GEC to get the added length needed to reach. Would be using Brady crimps for the splices. Area of splice in area not normally considered "subject to damage". Any reason the splice would need to be in an enclosure of some sort?