Soo, I designed this PV system with a load side tap after a 100A breaker at the meter main that's feeding a subpanel inside. Of course, a 100A breaker will be installed downstream at the subpanel. Basically we're tapping between two breakers, which should be totally fine as long as my PV output doesn't exceed the rating of these feeder conductors. However, I got this inspector telling me that the feeder conductors that I'm tapping into need to be 25' or less according to Article 240.21. For some reason he believes that once you tap a feeder conductor, the feeder conductor itself becomes a tap conductor as well. Has anyone heard such a thing before?