I will soon be installing a 16kw standby generator along with a ats for a friend. He wants to run his central a/c on it, nameplate says min circuit ampacity is 15.5a, I'm assuming this is it's running amps. I didn't get a look at the airhandler yet. I was thinking about installing a time delay in the condensing unit after the transformer that powers the t-stat to avoid the unit from immediately kicking on with everything else on the ats. Haven't installed a time delay for this type of application, anything I need to know? Hooking the timer up in the manner I described will also delay the air handler right?