I just bought a condo, so the panel in my unit is a subpanel, I just noticed that they have the nuetral and ground bonded! I almost S#!T my pants! I s this why all my electronic dimmers keep burning up and malfunctioning?
Seriously doubt it. Don't think you would notice a thing with dimmers or anything else for that matter. Might have caused some radio interference problems though, but that is a big maybe.I s this why all my electronic dimmers keep burning up and malfunctioning?
Sparks no offense, but the multi-grounded neutral does not have anything to do with your dimmer problem. They are two separate issues.how about the lights flickering when the dimmers were set at a certain position? just trying to troubleshoot this...I never ran into this before!?
Sparks if your multi family dwelling is older, it is common to not have a disconnect outside You would just have a bunch of meters. No isolated grounding conductor.
We just finished a condo investigation.There was over 40 amps of ground current in a 300 unit complex.Water was turning green/blue and smelled like rotten eggs.Peoples hair was turning green when they washed it ,good luck,I will never buy a condo!