Have 5 runs of 400 coming from pad mounted utility transformer running underground 200 feet to switchgear. 208 with neutral. Utility company does not want my grounds entering their transformer. Do I originate my ground at the first means of disconnect(the gear) or do I have to pull a ground with the service? By the way it is PVC and Rigid.