Got written under 250.119 for using a nice black insulated ELECTRODE grounding conductor out to the ground rods. Came into a big bunch of thhn #4. 250 .62 is the proper code reference for the electrode grounding conductor which says you are to.use bare,covered,or insulated. Nothing about color. Inspector wants me to falsely identify the conductor. Any feedback?