Was at a residence the other day were the utility primary and grounded conductor broke at two diferent locations. With this it sent HV to the service equipment energizing the neutrel and equipment grounds in the house. A fire started at the oil furnace burner. The grounding electrode system was intact. The voltage in the ground even burnt the metal expation joint in garage floor. Any comments on what more to do to prevent this in the future?