I missed 300.3(B)(3) as others have stated that would allow the use of only one 14/3 NM to carry the needed neutral and use 14/2 NM for the other two cables.
Thanks to all
Good for you, there are some that are not getting this someway , talking dead ends and things , and neutral in every box, 1 - 14/3 between every box gives you a neutral in every box . I believe some are not understanding you are using 1 circuit and 3 gang boxes . :grin: