That strap and green screw below the lower breaker, is that a factory neutral-ground bond? So the panel is marked "Suitable for Use as Service Equipment?"I have a set of SECS not a feeder that's the whole argument I believe
The breakers are not in parallel, unless their load sides are connected together.There's something weird about that drawing. They call the top breaker the main, but both breakers are in parallel.