That strap and green screw below the lower breaker, is that a factory neutral-ground bond? So the panel is marked "Suitable for Use as Service Equipment?"I have a set of SECS not a feeder that's the whole argument I believe
There's something weird about that drawing. They call the top breaker the main, but both breakers are in parallel.