I'm confused regarding 215.2 (A) (1). How to size feeders that less than 600v based on the continuity of the load (1.25*continous+continous) regardless the correction factor (catalog ampacity only). It means when we have correction factor 0.5 & according to continuity rule the conrinuity is calculated after demand, so the actual ampacity will be less than the demand. Is it ok?
24.9 KB Views: 1