my brother is working on a restaurant job that has a 1 phase, 240 v service, 34 kva padmount xfmr. From the secondary side of the xfmr they ran 3 500mcm copper wires to a 4 bank meter socket that has 4 200 amp load side circut breakers. From each 200 amp breaker they ran 4/0 ser cable to 200 amp panels. Most of the kitchen equipment is gas fired, the biggest load is 2 ten ton AC units. It seems to me that 4 100 amp panels would be the max for this situation. Thanks in advance for any help.