The electric meter is located on the utility pole which is probably 75' from the house. Over head service to house to service mast then into panel board. There is no grounding rod outside the house for the panel board, there is no grounding rod located at the meter. There is a grounding conductor running down the side of the pole into the ground servicing the coductors on the pole. Water service inside the house is also not grounded/bonded to the panel. Where should the grounding rod be located for this type of situation? This is in an older section of town and I beleive this is a isolated situation.