Does the typical light switch not serve as a "disconnect" for "fastened in place utilization equipment" ? I've always thought about it that way, aside from three-ways of course. Might be opening Pandora's box w/ this one... just some food for thought.How about something as simple as " the wall switch need to be installed within "X" number of feet or inches from the opening side of the door jamb. Maybe throw in a height requirement/restriction.
Dare I suggest that all lighting circuit branch circuit OCPD's be lockable and risk crucifixion by the forum, lol.