as the code reads in 210.52b3 receptacles installed in a kitchen to serve countertop surfaces shall be supplied by no fewer than two small appliance branch ckts. As it states we need two circuits, refridgeration equipment is also allowed to be covered by this section. My question, is the refridgeration outlet accepted as one of the two circuits or is it in addition to. I have a seperate circuit for the disposal, dishwasher and microwave/hood combo. I am using a seperate circuit for the refridgerator also and the kitchen only has 4 receptacles total.