When the panel is located far away from the meter, a disconnect box next to the meter, as well as 4-conductor SER cable is required. Normally #2 SEU cable is good for 100A service. However, table 310.15 says that SER cable would be good for only 90 amps. Would I be allowed to install a 100A breaker in the outdoor disconnect, or would I be limited to 90A? I've seen most of these with 100A breakers in them.