How many here pull 2 circuits to feed the required 20A laundry circuit? I was trimming out a house today and happened to see the nameplates on the washer and dryer. The washer was 10.0A/120V and the gas dryer was 11.8A/120V. I have never taken the time in the past to look at the info because the units are never usually there yet when I finish. I have never had a callback where overload tripping was an issue, anybody here run into any issues with this? Is it possible that the newer units require more Amperage and this may just start to become a problem? Thanks.