I just reread 210.52(C)(1). Can someone explain the logic to me? Why would you ever want a receptacle behind the sink or cooktop? I think it is pretty much guaranteeing that the cord will drape across the stove or the sink. I just don't see why the code body thinks this should be REQUIRED. Isn't the NEC supposed to require things that enhance safety?