I was helping our hvac guy to track down why his control voltage transformer was frying. noticed the secondary side one line was bonded tothe frame of the hvac equipment which was bonded to the equipment grounding conductor. he stated this was how he found it. so we hooked up another x-fmr. it also blew. we took the ground off and the next one held. is the secondary side supposed to be bonded or not.